COMPLETION NOTES: Customer has informed GreenergyAir HVAC technicians that someone was out yesterday (07/02/2022) and replaced a valve. This coil doesn't have a valve it's a piston type coil, which usually doesn't control refrigerant very well, when it's over two tons. This is a 2.5 ton system. The pressures are jumping all over the place technicians have included two separate pictures (video is available if needed). There's essentially no superheat and subcooling, which means the coil is getting the proper flow of refrigerant. GreenergyAir HVAC technician suggests to come back with a refrigerant, but the the solution would be to replace the whole coil with an expansion valve type coil. Our technicians could retrofit the system with an expansion valve, however, if there's something wrong with the actual coil like it's clogged up inside of one of the capillary tubes, then it will be a waste of money. Hence, we recommend to replace the whole coil with one that has an expansion valve for 2.5 tons, take all the refrigerant out and put in new refrigerant to make sure there's no air in the system and leak check. Technician's suspicion is that the system is low on refrigerant also. But there's no way to tell without the correct superheat readings in the correct pressures.
July 15, 2022
Technician: Mark Haas
We provide exceptional services and are a one-stop-shop for our clients. Our expert team delivers high-quality design and installation services on time and within budget. We exceed our clients’ expectations through our dedication to outstanding customer service. Our money-saving service and maintenance contracts give our clients peace of mind. Contact us for more details.
What do customers say about our work?
When my AC stopped working, Greenergy was able to come the same morning that I called. Mark was very helpful and professional and was able to fix the issue in under an hour, replacing a broken capacitor and conducting additional diagnostics to make sure everything was running optimally. Very much appreciated!
Mark was great and professional. After three days of no air conditioning we were dying. He quickly identified the problem to get our house cool again. Highly recommended
Mark and Alec were very nice and professional. They came in and identified the issue quickly. Fixed us up in less than 40 minutes. They replaced the dual run capacitor.Even followed up the next day to check in on the repair.I recommend this business, they are knowledgeable and easy to work with!!
We had a great experience! After another company came out twice saying nothing was wrong, Mark came and was able to look at our AC unit and get us a new one all within 24 hours. Very professional, quick, and overall great service. Thank you!
Reliable and Efficient AC Repair Service!I am so impressed! We had a malfunctioning ac unit in the hottest of days and Mark and his team came to fix it. They were professional and efficient!What I loved about them the most is that they circled back with me later on in the day to make sure everything was working correctly. I can't think of a business I have worked with recently that had that type of commitment to excellence. People don't do business like that anymore and its refreshing to see. I appreciate it. They made sure I was completely satisfied and I would not hesitate to use them again. They not only fixed them, they washed them!
These folks are amazing, they immediately responded when my A/C went out and were super professional, knowledgeable, and nice. Mark and Alec worked hard to repair my unit in a timely manner, and saved my life in the midst of this heat wave! Highly recommend!!!